Validate your login
Create New Account
Plain annealed copper wire, solid class 1 or stranded class 2 according to EN 60228.
Mica/Glass fire-resistant tape covered by high-performance fire-resistant silicone rubber type El2 to BS EN 50363-1.
Insulated cores are cabled together.
Uninsulated tinned copper conductors of the same section and class as the insulated conductors in the 2,3 and 4-core cables.
Drain wire of 0.5 mm2 tinned copper conductor is provided in cables with more than 4 conductors.
LSZH thermoplastic material type LTS3 according to BS 7655.
Colour red or white (other colours on request)
-40DegC to +90DegC
FIRECEL SR 114E are primarily intended for use in fire detection and fire alarm systems, emergency lighting circuits or if cables need to property operate when fire resistance improvement is required.
Typical applications are:
. BS 5839-1 for enhanced fire resistant cables in fire detection and fire alaram systems for building
. BS 5839-8 for voice alarm systems
. BS 5839-9 for emergency voice communication systems
. BS 5266-1 for emergency lighting of premises
. BS 8519 for fire-resistant control cable systems for life safety and fire-fighting application - Category 2
Cable in one drum:
Pallet weight :
Total net weight including both :